|Edition Number:||1||SCC Approved:||--|
|Edition Date:||2012-10-19||DOD Approved:||--|
|Price Code:||B||ANSI Approved:||2018-01-08|
188.8.131.52 This standard applies to isolating equipment incorporating electromechanical contactors remotely controlled and monitored to provide remote isolation status indication with a defined integrity level. This equipment is intended for use as an additional isolating means on the load side of the required supply-disconnecting device and over current protection. This standard applies to isolating equipment that is to be used in circuits of which the rated voltage does not exceed 1000 Vac or 1500 Vdc.
184.108.40.206 The system isolation equipment is expected to be used both as a means for removal of power for prevention of unexpected start-up of a stopped machine and as an isolator to provide protection from electric shock by ensuring the removal of electrical energy.
220.127.116.11 This equipment is intended for installation in accordance with the National Electrical Code, NFPA 70 and the Electrical Standard for Industrial Machinery, NFPA 79:2012.
Note – Reference to System Isolation Equipment is found in Article 430.109(A)(7) of the National Electrical CodeNFPA 70; in Clause 5.5.4(3), Devices for Disconnecting (Isolating) Electrical Equipment, of the Electrical Standard for Industrial Machinery, NFPA 79:2012; and in Clause 5.3.2(d) of the Standard for Safety of Machinery – Electrical Equipment of Machines – Part 1: General Requirements, IEC 60204-1.
18.104.22.168 The System Isolation Equipment is not intended to fulfill the function of a motor starter or other motion control device.
22.214.171.124.1 The system isolation equipment is principally intended for industrial machine applications where, isolation of power is so frequently required that the mechanical life of a typical disconnecting means is unacceptably short or where there are multiple entry points on the machine where disconnection is required, or both.
Note – Multiple entry points are a function of access needs and the layout of the machine.
1.2.1 The object of this standard is to state:
a) The characteristics of the system isolation equipment;
b) The conditions of operation and behavior for the system isolation equipment, its dielectric properties, and the degree of protection provided by its enclosure where applicable;
c) The information to be marked on or given with the system isolation equipment;
d) The normal service, mounting and transport conditions of the system isolation equipment;
e) The construction and performance of the system isolation equipment;
f) The tests intended to verify that these conditions have been met, and the methods to be adopted for these tests.