UL Certification Customers have free access to UL Standards, not including UL IEC Based Standards. UL Certification Customers may access published Standards materials by using the Standards Certification Customer Library (SCCL) at ULstandards.com.
Not sure if your company already uses the Standards Customer Certification Library website? Then contact customer service at 1-888-853-3503.
ALL UL STDS for CANADA
1.1 These requirements cover fixed electric duct heaters, and remote control assemblies for such equipment, rated at 600 volts or less to be employed in ordinary locations in accordance with the National Electrical Code, ANSI/NFPA 70.
1.2 These requirements do not cover fan-coil units, central heating furnaces, panel or cable type radiant heating equipment, electric boilers, baseboard heaters, air heaters, nor any other electric heating equipment or appliances which are covered in or as a part of separate, individual requirements.
1.3 Duct heaters intended for use in a hazardous location are judged on the basis of its compliance with the requirements in this standard, together with the requirements for hazardous location equipment included in other applicable standards.
1.4 Duct heaters designed to be connected to air-duct systems are intended for installation in accordance with the Standard for the Installation of Air Conditioning and Ventilating Systems, NFPA 90A, and the Standard for the Installation of Warm Air Heating and Air Conditioning Systems, NFPA 90B.
1.5 These requirements apply to relays and other auxiliary control devices that may be provided as part of a duct heater to make it usable with other heating or cooling equipment, and are intended to take into account the effects of operating the duct heater in conjunction with or in proximity to such equipment.
1.6 A duct heater is a self-contained heater designed to be installed in the field in the air stream of a ducted system, external to the air-moving unit. It is designed to be installed in a duct where an adequate flow of air from a separate, interlocked fan or blower system is provided. Such a heater may be located in the main supply duct of an air heating system, or in one of the branch ducts. Two or more duct heaters may be installed in a group (in proximity to one another in the duct) if tests indicate acceptable results when the heaters are installed in accordance with the manufacturer's instructions.
1.7 A duct heater intended to be employed in conjunction with another source of heat is judged on the basis of its compliance with the requirements in this standard, and further examination and tests to determine whether or not the combination is acceptable.
This revision of ANSI/UL 1996 dated August 30, 2022 includes alternate compliance paths for UL 873 and UL 353: 184.108.40.206, 220.127.116.11, 21.1, 22.5 and 23.3.2.
RevisionsRed Line Std. (12)
CSDS Proposals (12)
An electronic document associated with a UL Standard for Safety or Outline of Investigation, and issued by UL to propose:
UL LLC CRD (2)
Other Updates (0)
Referenced Standards (32)
Reverse Referenced Standards (1)
The cost to purchase this Standard varies depending on whether you are ordering a hardcopy, PDF or combination of the two. We also offer two different types of subscriptions: a one year and a three year.
You will be able to choose your purchase options on the following pages.
To serve you better, please update your account details.